Blokset U drawer cabinet design instruction
1. the basic modulus are: 2M/2, 4M/2, 2M, 4M, 6M, 8M, 10M, 12M
2. There are two protection schemes:
1) traditional power distribution and motor protection scheme
2) intelligent power distribution and motor protection scheme (iPMCC)
3. effective installation height is 40M (1M=50mm), CB chamber and busbar chamber are included. The CB chamber modulus height are as following references:
Double horizontal busbar (>4000A)
single horizontal busbar
4. using mode:AC-3 50/60HZ
5. Rated voltage: 400/690V
6. There are maximum two groups of secondary connectors for drawer whose modulus is more than 4M, totally 48 points.
7. There is maximum 1 group of secondary connectors installed in 2M/2, 4M/2, 2M drawers, totally 24 points.